601 Gateway Blvd.
South San Francisco, CA 94080
Onsite parking lots around the building contain spaces for 1,216 cars, and the structured garage contains spaces for 1,800 cars. The on-site security staff patrols the parking lots throughout business hours. Paving is typically asphalt and sidewalks are concrete, with granite pavers at the building entrance plaza. Parking at a ratio of 3.3 spaces/1,000 rentable square feet, or 2,963 spaces are available for tenants' employees and visitors. Exterior lighting is high-pressure sodium for the parking areas and metal halide for the walkways. There are 16 handicap accessible parking stalls directly adjacent to the building.
Energy management at 601 Gateway begins with proper preventive maintenance and repair of the installed systems. From this point, good operating strategies--i.e., retrofitting lighting fixtures using reflectors, T-8 lamps, and electronic ballasts along with variable speed drive technologies on the central plant chiller, cooling towers, and main supply and return fan systems--have provided ongoing energy efficiency opportunities in operation. The addition and enhancement of the Andover building automation system has further allowed a more integrated approach and connection to the field systems and components, giving the building management team the flexibility to make the overall system operate more effectively and thereby more efficiently.
The replacement of the domestic water booster system with a new variable speed drive integrated system in 2007 added additional efficiencies in the domestic water system. In 2009-2010, the build out of four floors with current codes and certification efforts under the U.S. Green Building Council's (USGBC's) Leadership in Energy and Environmental Design-Commercial Interiors (LEED-CI) rating system will continue to enhance the building's energy performance in the future. This LEED-CI effort replaced lighting with T5 lamp and ballast technology as well as occupancy sensor control of the lighting system and LED task lighting at the workstation level. They also included new direct digital control (DDC) integrated HVAC variable air volume (VAV) zone boxes and controls. These floors and improvements were awarded with LEED-CI Silver certification in 2011.
In 2010, the shared parking structure underwent a lighting retrofit of over 500 light fixtures from the traditional HID system to T8 florescent fixtures. The project achieved substantial reductions in both demand and consumption by replacing the existing HID fixtures at 215 watts per fixture with new T8 fixtures, lamps, and electronic ballasts that use 55 watts per fixture in comparison. In addition, the perimeter fixtures were outfitted with photocell operation to take advantage of daylight reductions. All in all, we achieved a 70-percent reduction in demand and consumption from this one lighting project.
Please note: Narrative information in this profile has been provided by Boston Properties or a representative of this facility. Other building information was verified and submitted to EPA at the time of application. Building energy performance, operating characteristics, and ownership/management may be subject to change over time.
Year(s) Labeled (Rating):
Facility Type: Office
Total Floorspace: 215767 sf
Year Constructed: 1984
Contract Type: None
Financing Type: Internal Capital
|Stage 3-Load Reductions|
|Stage 4-Fan Systems|
|Stage 5-Heating and Cooling Plant|
For More Info:
Director of Engineering
San Francisco, CA 94111